PC CLASS dual power Automatic transfer switch duplicate supply HEREINDFTER ATSE
S series of PC-class dual-power supply automatic switch (hereinafter ATSE) is the latest company Technology devel opment of high-tech products. It is in line with GB/T14048.1-2006, GB/T14 048. 11-2002 superscript, And also with "high-rise buildings fire norms" and "Architectural Design fire norms", "emergency Lighting Design Guide, "" civil el ectrical des ign specifications. " Product component, parts after martial law Screening of the aging grid, finished a continuous 168 hours of electricity a dry run, the final passthrough the test load Before the factory. This is t o ensure the product's reliability and security.
ATSE apply to AC 660 V, rated frequency of 50 Hz/60Hz. 250 volts DC and the following Occasion. The products are mainly used for the state of a load, widely applicable to the fire, postal communication, hospitals, hotels, Urban rail transport and high-rise buildings, industrial assembly line, television stations
need electricity for the important parts. Main power Emergency Power can be power grids, with Self-excitation generator sets, battery, and so on.
Ambient air temperature
Ambient air temperature of -15 to +60 , and a 24-hour average temperature does not exceed +55 . Around +65 air temperature is above or below -20 users should consult with the manufactures.
The maximum temperature of +40 the relative humidity of not more than 50 percent, the largest of 90% relative humidity, ability Humid air by the impact of the sea, at a lower temperature may allow a higher relative humidity, Occasionally the temperature under Congeal Dew should take special measures.
Location on the place no more than 2,000 meters above the sea level. For a higher altitud e, taking i nto account the air Xinhua strength and cooling down, in consultation with the Manufacturer.
Pollution levels Installation on grade III
Installation sort Installation sort IV type
Products in the cabinet fixed installation, the largest inclination to 22.5
In AC 380 V-arc distance of 80 mm. AC at 660 V-arc distance of 100 mm. Under 125A installation do not consider flash arc.
Use category AC-33B
Wenzhou Chizhou Electric Co.,Ltd.
Wenzhou Chizhou Trade Co.,Ltd.