Products feature and character
CZQ2 Series intelligent dual power automatic swithes is made up of two units in 3 pole and 4 pole of MCCB and (auxiliary contacl,alarm contact),the mechani cal interlo cking transmission,intelligent controller and other components. It has the integral style and split type with two kinds mechanism. Integral controller is equipped with a base and executing agencies ; Split type is intelligent controll er installe d in the panem User take the base by implementing agencies to install into the cabinet controller with about 2m cables.
Reliable mechanical interlock between the two circuit breakers and electrical in terlock dev ice .Eelimin- ate the two devices closing completely at the same time.
SCM intelligent controller used to control the core hardware is simple and powerful, expansion of conv- enience, high reliability.
It has a short circuit, over load protection functions, over voltage,under voltage, loss phase automatic transfer function andintelligent alarm function.
Automatic switching external parameters can be set free. Operation of Intelligent motor protection
The control circuit devices with fire, fire control cente r to a cont rol signal into intell igent controller. Two sets circuit breaker will enter a stating of breaking .
There is a computer network interface for achieving remote control four remote telemetry functionsThe feature and character of CZQ1 series ATS
CZQ1 series ( terminal type ) (economic type ) - Automatic Transfer Switches, is used to the terminals to the dual electrical power switching devices;
Small in volume,simple in constitution;
There is provide 2P,3P,4P.Easy to operation and long to use;
Transfer switch driving by single motor, a smooth, no noise, the impact is small;
With mechanical interlocking and electrical interlock , change over credibility , could be supply by man- ual or automatic operation;
Common, spare circuit breaker rated current can be different;
A.T.S contain connector for users wiring can rdflect Breaker (open or closed) state;
A.T.S panel show various instructions: separations instruction manual, automatic and wiring diagram and so on.
Use of Operates and supports
Whether main power or backup power with voltage or not, all can be by manual mode ope rated.Under manual,put the auto- manual but ton to manu al position, pull the handle by clockwise to end,Backup power implementation circuit breaker Qr i s OFF, implementation of MAIN power supply circuit breaker Qn ONg; When pull handle counterclockwise to the end, the implementation of Backup power source Qr is ON,implementation of MAIN power supply circuit breaker Qn is OFF;
Set the auto position, if the MAIN power is normally,ATS will transfer to MAIN power working.The MAIN POWER indiacation will bright on panel;If the MAIN power is unusually,ATS will t ransfer to Backup Power working.The Backup indication will be bright on the panel.
ATS has 1A of two units fuses and a elec tric connector, fuse as short-circuit protection in automatic controller.Electric connecto as dry contact in In dication light to panel of controller box,v oltage of 220V AC, l50mA , the detail please reference to instruction.
Fault Analysis and Removal
When ATS under automatic control state,the POWER condition was changed,but the operation mecha- nism no action. Such as MCB can't closed-transition or open - transition then should be checked: 1.whether the power grid are failured;
2. whether the wiring shedding;
3. the fuse itself whether burning. If the front point of one circuit breaker with ele ctricity, and th e conne- ction are botht wiring well, fuses are intact, but yet can not closed-transition or open-transition.You should be asked to professionals or contact manufactory.
Notice to users in orders
When User place the order need to notice the identifying device model s, spe cifica tions, dis pensed breaker models, speci fications, pole number. Such as : Automatic Transfer Switch device, Self-input and Self-recovertype, rated current of 50 A,4 pole, which is written CZQ1-63L/4P (50A).
For users special requirements, please contact with factories and to explain well in orders indicate.CZQ1] Technical Parameter of CZQ1 tye A.T.S.
|Poles||Rated voltage Ue(V)AC||Rated Current In(A)AC||Frequency (Hz)||Control voltage (V)||Transfer time||Mechanical life (times)|
|6, 10, 16,|
20, 25, 32,
40, 50, 63
When common source is n ormal, the functional key is at position "auto", reserve breaker is open and common breaker is closed to protect common source for connecting with load,the common power voltage indicator is light.When the common source failures (the voltage is lower than 60% of rated voltage), the common source will transfer to reserve source automatically, the reserved source voltage indicator is ON, the reserved source working indicator is ON. After removing the failure of the common source,this swi tch will transfer to the common source automatically again.
Wenzhou Chizhou Electric Co.,Ltd.
Wenzhou Chizhou Trade Co.,Ltd.www.chccz.com